There are so many factors that can affect the gas pressure that we recommend an onsite inspection and professional recommendation by a LP gas professional. However, we are able to provide you with the fuel consumption rates and required water column which will help provide the correct size needed for installation. The required fuel pressure to the generator fuel inlet at all load ranges is 10 to 12 inches of water column for LP gas. Fuel consumption at full load is 2.9 gallons/hour. For additional information, please consult the spec sheet at http://www.generac.com/SpecSheets/0...
answered 2 years, 7 months ago